For the 115 VAC 4 In/2 Out Analog Block - Phase B (IC660BBA100), configure points %GD0 through %GD6, where:
%GD0 is the Block-Level diagnostic point.
%GD1 through %GD4 are the Circuit-Level diagnostic points for inputs.
%GD5 through %GD6 are the Circuit-Level diagnostic points for outputs.
Note: If you do not configure %GD0, no fault data is collected. If you do configure %GD0, but do not configure points between %GD1 and %GD6, messages for the missing points are generated in the Status Log at startup and whenever a fault occurs.
All diagnostic points are Analog device points with a Point Type of USINT. The Update Criteria is On Change for the Block-Level diagnostic point and Unsolicited for the Circuit-Level diagnostic points.
Prior to receiving fault data from the block, you must enable outputs to it.
Genius fault data.