The Honeywell ABC Diagnostics program, hwabc_diag.exe, may be used to verify hardware installation and communication operation.
To run the N2 diagnostics, execute the following command:
hwabc_diag.exe <port> <network drop #> <Baud > <Parity>
<port> is the name of the port connected to the connection cable.
<network drop #> is the network nodal address of DCM which can be from 0 to 31. The default value is 0.
<Baud Rate> has a default value of 9600.
<Parity> is none by default.
For example, if your connection cable is attached to COM2, network drop number is 2 for the DCM, baud rate is 9600 and parity is none, execute the following command:
hwabc_diag.exe COM2 2
The Honeywell ABC Diagnostics program will open the port and read values of a few points:
Comm parameters: drop 2, baud = 9600, parity = no
Installation verification procedures.