Product : ISaGRAF 3.x
Date : 1-October-2001
File : OPC Server V2 with ISaGRAF 3 target.htm
Subject : How to use the OPC server V2 with ISaGRAF target
Guidelines to use OPC server V2 with a ISaGRAF 3 target.
Select the communication parameter in the workbench. Note that these parameters will also be used by the OPC sever to connect to the target.
Note that it is not mandatory to download the symbol table. Indeed, the server will browse the symbol from the project directory in the workbench. In order to specify this path, follow step 4.
From your HMI you can browse the variables.
If you want to connect the OPC server and the ISaGRAF Debugger, you need two communication tasks on the target side (Twice ISaTST for serial link or twice ISaNET for ethernet, or a mix of both).
In this case, download, connect the HMI, then change the link setup from the workbench in order to connect the debugger with the other communication task.
Copyright © 1996-2009 ICS Triplex ISaGRAF Inc. All rights reserved.