Alarm Delay Time in milliseconds. Specifies the time in Milliseconds for a tag to be beyond an alarm limit, before an alarm state is generated. The idea is to prevent noise or an alarm bouncing near an alarm limit. The SCADA node waits this period of time before sending alarm messages, if during this waiting period, the tag returns to a non-alarm value, then no alarm message is generated. If Reflect On Line changes to Database is enabled, changes will be saved in the Configuration Database on the Project Node (i.e. become permanent).
0 - 6,000,000
Field Type: Analog
Configuration: Alarm Delay Time
Tag fields: .DELAYA
See Also, 22.214.171.124 Alarm Delay Time